Bigger properties and Stately Homes
A Stately Home manager asked us to evaluate the best means to resolve the issues they have when a fault occurs. They had been going back and forth between, plumbers, electricians and boiler engineers.
After a lengthy survey, we reported on our findings, making suggestions as to where money could be saved.
The suggested were:
Also, we had to resolve issues with the water not returning back to the cylinder above 50 degrees, so a plate heat exchanger was fitted. We later changed the cold water storage tank, ensuring water was exchanged regularly preventing stagnation and this also remedied a leaking tank.
A dripping oil fill point into the tank area was changed to a cabinet oil fill point with a catchment tray ensuring no contamination occurred.
The pictures below show the new heating pumps, speed controllers and Honeywell weather compensator and various other parts of the system.